Warmup Snow and Ice Melting Mat 40 sq ft - WSMM$459.00
Warmup Snow and Ice Melting Mat WSMM - 40 sq ft
Available Voltage: 240 and 480 Volt
for use under Asphalt, Concrete or Pavers
Warmup Snow Melting Mats are uniquely designed for snow melting in parking lots, driveways, pavements, stairs, etc. with total safety. They are suitable for embedding under concrete, asphalt or under pavers. Come with a 10-Year warranty.
Mat Spec and Coverage
240 Volt - Mat Size 2' x 20' - Resistance 8.3 - Amps 28.80 - Watts 2000
480 Volt - Mat Size 2' x 20' - Resistance 4.16 - Amps 115.38 - Watts 2000
- 16ft cold lead, single point connection
- Easy roll-out installation
- Installation in sand, gravel or on wire mesh.
The WSMM (Warmup Snow Melting Mat) is commonly used in concrete pours, asphalt driveways and paved walkways. All Warmup Mats are rated for 208-240-277V applications. Mats are 2ft or 3ft wide and with a cable spacing providing 50w/sqft for optimum results under even the harshest conditions. Embedded up to 4” deep, they can be laid out as tire-tracks or for full coverage designs.
- Operating voltage - 240V & 480V
- Output rating - ± 50 W/sq ft
- Mat width - 2ft or 3ft wide
- Lengths - Range from 5' (152cm) up to 60' (1828.8cm)
- Construction - Energy efficient twin-conductor heating cable of 1/4” (6mm)
- Maximum temperature - 464˚F (240˚C)
- Cold tail length - 16.4’ (5m)
- Warranty - 10-Year
Suitable Coverings - Pavers and related masonry, Asphalt (direct contact or indirect contact), Concrete (not lightweight)
Suitable Base - Crushed gravel base, Sand bed, Insulation sheets
Min. coverage - 2", Max. coverage - 4"
Installation under PAVERS - Cables should be covered with 2" of sand for paver application. Pavers to be maximum 4" thick.
Installation under ASPHALT - Cable will withstand direct asphalt contact for limited time until asphalt cools. For pours hotter than 220F, apply a layer of 2" of sand over the cable prior to laying asphalt. Do not use rollers over 2 Ton. Hand-rolling highly recommended.
Installation under CONCRETE - Ensure the pour is 4" maximum over the cable. Use re-mesh or wire mesh to secure the cable in the middle of the pour for deeper pours. Cable/Mats can be zip tied to mesh and mesh can be raised with bricks or pulled during pour.
WARRANTY & MAINTENANCE - When installed according to the installation manual and proper testing has been performed throughout, the system requires no maintenance for the duration of its warrantied life. The WSM cable is warrantied for 10 years against manufacturer’s defects and is protected by Warmup’s SAFETYnet guarantee.